Sampling and monitoring
Sampling of Private Water Supplies
The Private Water Supplies (England) (Amendment) Regulations 2018 and the Private Water Supplies (Wales) Regulations 2017 require local authorities to demonstrate that the sampling, transportation, and storage of private water supplies complies with the ISO/IEC 17024 standard. Local authorities will be aware that DWI has developed a sampling procedures manual to assist local authorities comply with this requirement. Any individual collecting, transporting and storing samples of private water supplies must demonstrate compliance with the scheme sampling manual. In practice this means gaining certification, following training and attainment of the required pass criteria on assessment.
CATG are the nominated certification body responsible for maintaining the ISO17024 accreditation, as well as training and awarding certification of successful applicants.
CATG has confirmed that the accreditation to the ISO 17024 standard is expected imminently and, as such, are in a position to take bookings for training from those requiring certification under the scheme. Due to the ongoing CoViD-19 crisis it is possible this process may be delayed. Local authorities should make enquires with CATG to discuss the situation and explore if there are ways to work within current Government social distancing requirements.
Local authorities are advised to complete the required certification as soon as possible and as Government guidance allows. Local authorities should contact CATG regarding the availability of courses on 01524 400632 or via their website at https://www.catg.co.uk/contact
Further information on the certification scheme can be found here: the scheme (PDF125KB); and further information on sampling can be found here: the sampling manual (PDF465KB, or on the Inspectorate’s website.
Local authorities are advised to familiarise themselves with these procedures.
DWI will be monitoring progress with training and accreditation, and will report on the position in our annual report.
Sampling and monitoring for Regulation 8 supplies (private distribution systems)
The monitoring of each Regulation 8 supply must be based on the outcome of the regulatory risk assessment carried out for that supply. The relevant parameters and frequency of sampling should reflect the risk rating and the nature of the hazards identified in the risk assessment:
- coliforms and E.coli (ingress into the network or poor hygienic conditions, especially tanks)
- colony counts (upward trend may indicate deterioration of water quality)
- conductivity, hydrogen ion and turbidity
- iron and zinc (from corrosion of galvanised steel or cast iron pipes), manganese, aluminium
- taste and odour (ingress and permeation of plastic pipes)
- trihalomethanes and bromate (disinfection by-products) (especially if there is chlorination within the private distribution network)
- lead, nickel and copper (from the pipe work or tap fittings in the private distribution network or within the premises
Sampling and monitoring for Regulation 9 supplies
There are two types of monitoring for Regulation 9 supplies (excluding supplies to tenanted dwellings in Wales, which fall within regulation 11 of The Regulations (Wales))
Monitoring of Group A parameters
The purpose of monitoring for Group A parameters is to:
- determine whether or not water complies with the concentrations or values in Schedule 1 of the Regulations
- provide information on the organoleptic (taste, odour and appearance) and microbiological quality of the water
- establish the effectiveness of the treatment, including disinfection.
The parameters, ammonium, coliform bacteria, colony counts, colour, conductivity, E.coli, hydrogen ion concentration (pH value), odour, taste and turbidity, must be monitored in all large supplies at the check monitoring frequency.
Monitoring of Group B parameters
The purpose of monitoring Group B parameters is to:
- determine whether or not the water complies with the concentrations or values in part 1 or 2 of Schedule 1 of the Regulations, other than Group A parameters already being sampled under part 1 of Schedule 2 (the standards and indicator parameters).
- check (where disinfection is used), that disinfection by-products are kept as low as possible without compromising the disinfection.
The likely sources of individual parameters table (PDF 26KB) provides information on likely sources of specific parameters within a private water supply. Criteria that could be used to decide on exclusion of a particular parameter from audit monitoring is given in the Information Note on Regulation 7 (England) (Wales).
Variation of monitoring requirements for Group A and group B parametersA local authority may reduce the sampling frequencies required for a parameter, or cease to monitor a parameter (other than E.coli), but can only do so in accordance with the conditions specified in Part 2A of The Private Water Supplies (England) (Amendment) Regulations 2018 and Part 4 of Schedule 2 of The Private Water Supplies (Wales) Regulations 2017.
Sampling and Monitoring for Regulation 10 (England) Supplies and Regulation 11 (Wales) supplies
The Regulations require a local authority to monitor all its Regulation 10 supplies (except a supply to a single dwelling) at least every five years and more frequently if required by the risk assessment for the following parameters:
- Escherichia coli (E.coli)
- Hydrogen ion (pH value)
- Any parameter in Schedule 1 to the Regulations identified in the risk assessment as being at risk of not complying with the concentrations or values
- Any other parameter identified in the risk assessment as a risk to human health.
A local authority may monitor a private supply to a single dwelling for the same parameters listed above if it is concerned there may be a potential danger to human health. However a local authority can only charge for this service if requested by the dwelling owner or occupier.
Monitoring of radioactive substances
Regulation 11 (England) and Regulations 12 and 13 (Wales) of The Regulations requires that a local authority must monitor each private water supply in its area for radioactive substances. In England local authorities must ensure that this is carried out in accordance with the requirement of Part 3 of Schedule 3 of The Regulations (England), and in Wales Schedule 3 of the Regulations (Wales).
Further information came be found in the Information Note for regulation 7 found here:
Page reviewed: 11 June 2020
Page modified: 11 June 2020